- Special Sections
- Public Notices
The Levy County Health Department is warning residents who obtain their water from private wells that the recent river flooding may have made the water unsafe. And the department wants folks to call the department so their well can be checked for free.
If a well casing has been submerged by flood water, residents are warned to either use bottled water, or boil or disinfect all the water used use for drinking, making beverages, cooking, brushing teeth, washing dishes, and washing areas of the skin that have been cut or injured.
Common unscented household bleach (4 to 6 percent strength) can be used effectively as a chlorine disinfectant. Add 8 drops (about 1/8 teaspoon) of unscented household bleach per gallon of water, then let it stand for 30 minutes, repeating the procedure if the water is still cloudy. An alternative disinfecting method involves bringing water to a rolling boil for one minute.
If a well has been flooded, call the Levy County Health Department for information on how to sample your water free of charge and where to bring the sample for bacteriological testing. If the test reveals bacteria, the well and water system need to be disinfected.
It is important to disinfect both the well and plumbing water with unscented household bleach to ensure that all infectious agents are destroyed. If water treatment devices are used, remove all membranes, cartridges, and filters and replace them after the chlorination process is completed. The amount of chlorine determines the length of time you allow the bleach to remain in your system.
DOH recommends the following steps to disinfect a contaminated well:
• If the water is discolored before adding the bleach, run the water until it is clear for up to 10 minutes.
• Turn off and then drain your hot water heater— bleach is not effective in water above 105 degrees.
• Remove and replace charcoal filters after the disinfecting process is completed.
• To avoid adding contamination to the well during disinfection, clean the work area around the top of the well. Then remove grease and mineral deposits from accessible parts of the well head and flush the outside surfaces with 1/2 cup of unscented household bleach in 5 gallons of water.
• Turn off the pump. Remove the cap or the well plug on the rubber seal. There are many types of well caps and plugs. If you have questions, you should contact a licensed well driller. If you have a submersible pump, you may also want to contact a licensed well driller for advice on disinfection procedures.
• Consult the bleach chart and pour the recommended amount of unscented bleach (4 to 6 percent) solution into the well. Try to coat the sides of the casing as you pour. If you get bleach on the pump or wiring, flush it thoroughly with fresh water to prevent later corrosion.
• Re-cap or plug the well opening and wait 30 minutes.
• Turn on and, if needed, re-prime the pump. Open all of the faucets on the system one at a time. Allow the water to run until there is a noticeable smell of bleach. You may also want to flush the toilets. If you have outside faucets, you may want to direct the water away from sensitive plants. If you cannot detect a bleach odor, repeat the disinfecting process.•
• Turn off all of the faucets and allow the bleach to remain in the system for at least eight hours.
• Backwash water softeners, sand filters, and iron removal filters with bleach water.
• Again, open all the faucets and run the water until there is no bleach smell—for up to 15 minutes.
After disinfecting your well, the water needs to be tested to verify that it is safe to drink. Although unscented household bleach is effective against microorganisms, it will not remove chemical contamination that may have gotten into the well.
Contact the Levy County Health Department at 352-486-5301 for sampling instructions to get the water tested for chemicals. Fees for chemical testing have not been waived at this time.